Hello can you tell me if a 150watt light bulb 240v will be ok for the Sonoff Basic
i have 15 watts led panel light total 15 pcs ....can it be connected in single sonooff basic .....or required 15 pcs each ...trhanks
150VA / 240V = 0.625A The basic is rated at 10A so yes, it will handle it easily.
"15 watts led panel light total 15 pcs"
15W * 15 = 225W or 225VA
For 120V circuit: 225VA / 120V = 1.875A
For 240V circuit: 225VA / 240V = 0.938A
The Sonoff basic is rated at 10A into a resistive load. If you are pulling a heavily inductive load like a LED or CFL transformers or ballasts I would derate it by 30% to get the expected life out of the relay contacts. For that type load 7A or less should be okay.
i have 15 watts led panel light total 15 pcs
Then you have an inductive load of 225VA. Divide 225 by your voltage to get amperage.
For inductive loads I would probably try to stay below 7 amps. Inductive loads put more strain on the relay contacts.
15 x 15W = 225VA / Voltage = Amperage. So if your line voltage is 120 the 15 lights require a total of 1.875 Amps.
For an inductive load like LED transformers I would keep the Sonoff basic load under 7A to protect the relay contacts.
in het nederlands
taal ; nederlands
languase duch plaese
Hello, this article is very good for you, I have liked everything mentioned in this article and I will definitely share it in my friend circle... Thank you! Carrom Pool Mod APK